Wij hanteren het label Open Access voor onderzoek met een Creative Commons licentie. Klik op de licentie om de definitie te bekijken. Restricted access wordt gebruikt voor publicaties waar enkel de auteurswet op van toepassing is.
English - Summary
The Greenhouse at the Rutgers University EcoComplex is a prototype greenhouse. It demonstrates, amongst others, the working of hydroponics and aquaponics systems. The hydroponics system works by watering plants on a bench and filling up this bench until the roots of the plants are submerged in the water. The excess water slowly drains from these benches back into a central tank.
The water in the tank needs to meet certain conditions: the amount of fertilizer and pH of the water need to be maintained. This is done through a conditioning system which is controlled through the Argus control system. This conditioning system was not working before this project; the conditioning was done manually. The conditioning system was repaired and tuned to optimal performance in this project.
Next to that, the evaporative cooling (=fog) system of the Greenhouse had an issue. There is a major delay between closing the valves in the pipes that supply the pressurized water to the nozzles and turning off the high pressure pump: the valves turn off before the pump turns off. This delay of 8 to 10 seconds is bad for the pump. The delay is not acceptable and therefore it needs to be fixed.
This delay was minimized to 2 seconds in this project, which was acceptable.
This report gives insight in how these problems have been solved.